TITLE 77: PUBLIC HEALTH
CHAPTER I: DEPARTMENT OF PUBLIC HEALTH
SUBCHAPTER b: HOSPITAL AND AMBULATORY CARE FACILITIES
PART 205 AMBULATORY SURGICAL TREATMENT CENTER LICENSING REQUIREMENTS
SECTION 205.1760 GROUNDING
Section 205.1760 Grounding
In areas used for patient care or treatment, all receptacles operating at over 100 volts shall be grounded by an insulated copper conductor, sized in accordance with Table 250-95 of NFPA 70 (see Section 205.115(a)(1)(B)), and installed with the branch conductors supplying these receptacles.
(Source: Amended at 34 Ill. Reg. 7915, effective May 25, 2010)